26 kWMaximum power consumption
1.7 kWhVolume of cooled air
~ 3000 m³/hWater consumption per 1 kW of generated cold
0.3 gp/hLeave a request
Minimum maintenance, low electricity consumption, Russian-made spare parts.
The hotter it is, the more effective it is.
Instead of freon, the refrigerant is ordinary water, which gives out 100% fresh, filtered air during the cooling process.
The main component of TESSO air conditioners is a unique heat exchanger operating on the principle of regenerative indirect evaporative cooling (RIEC), in which ordinary water is used as a refrigerant.
The RIEC heat exchanger consists of alternating plates of capillary-porous material assembled in pairs. Passing through the heat exchanger, the hot air (full flow) is cooled in the channels formed by the plates.
The temperature of the plates themselves decreases due to the evaporation of water in their capillary-porous layer. The air moving countercurrent (auxiliary flow) evaporates water from the capillary-porous layer, is moistened and reheated through the plate wall, after which it is discharged into the atmosphere or for technical needs. At the same time, a much larger part (65-75% of the total flow) of the cooled air is sent to the consumer (the main flow).
Tesso is a modular system. If you need to get a more productive system, you can connect the BIO models to each other in any number. Each of the models can be equipped with a fan of different power, quantity and type.
The data were taken at an outdoor temperature of 113 °F and a relative humidity of 10%.
from 12000 m³The possibility of introducing equipment into existing cooling systems to reduce electricity consumption, taking into account the increase in cooling capacity. Leave a request
Gas turbine installations